Results 1 - 10 of 44
Results 1 - 10 of 44. Search took: 0.014 seconds
|Sort by: date | relevance|
[en] Experimental investigations were conducted on the direct expansion solar assisted Heat Pump (DESAHP). Refrigerant R-22 was expanded in the solar collector which also acted as the evaporator in a conventional vapor compression refrigerating machine. The experiments were conducted under conditions of high and low solar radiation, with evaporator completely shaded from the sun, and at night. System thermal performance was determined by measuring refrigerant flow rate, temperature and pressure at numerous points in the system. The results showed that 227-l of water could be heated from 3O degree to 55 degree C in about 105 minutes. Higher water temperatures were obtained during hot sunny days. The coefficient of performance of heating, COPh, ranged from 11 to 4.7, depending upon operating conditions. The total saving of electric energy during hot sunny days was about 460 %. It means that for 1 kWh of electrical input to the system, we achieve 4.6 kWh. This percentage decreases as the evaporator temperature decreases and is a function of solar energy input. (Author)
[en] In this paper, the exergy performance of direct-expansion solar-assisted heat pump systems working with R22 and R433A (mixture of R290 and R1270, 70:30 by mass) was experimentally assessed. The experiments were carried out under the metrological conditions of Calicut in India. (Longitude and latitude of location are and , respectively.) The artificial neural network model was developed for simulating the performance of a direct-expansion solar-assisted heat pump system to have realistic performance comparison. The experimental data observed during the year 2016 were used for training and testing the performance of network. The results showed that the network predicted exergy performance of a direct-expansion solar-assisted heat pump was found to be closer to the experimental results with a maximum fraction of absolute variance, minimum root-mean-square values and coefficient of variance. The system exergy destruction of R22 and R433A was found to be 1.36 and 1.25 kW, respectively. Moreover, R433A is identified as an energy-efficient and environmental-friendly alternative to phase out R22 in solar-assisted heat pump systems.
[en] Combined solar heat-pump facility for district heat supply of private dwelling houses is described. The application of the above facility provides for economy of traditional fuel-energy resources and completely meets the approved trend aimed at refusal from such generally accepted environmental pollutants as small-sized boiler-rooms, furnaces, etc. The system substantiation, calculations and parameters selection are presently completed. The facility design documentation is developed and the prototype production started. 4 refs.; 2 figs
[en] There are many different combinations of solar heating systems and heat pumps in the market; some of them differ considerably in terms of the design concept, control management and storage technology. One thing they all have in common is that solar heating comes first.
[en] Absorption heat pumps, first developed in the 19th century, have received renewed and growing attention in the past two decades. With the increasing cost of oil and electricity, the particular features of this heat-powered cycle have made it attractive for both residential and industrial applications. Solar-powered air conditioning, gas-fired domestic cooling and waste-heat-powered temperature boosters are some of the applications on which intensive research and development has been conducted. This paper describes the operation of absorption systems and discusses several practical applications. It surveys recent advances in absorption technology, including the selection of working fluids, cycle improvements and multi-staging, and fundamentals of the combined heat and mass transfer in absorption processes. (author)
[en] Growing concern about the depletion of conventional energy resources has provided impetus for considerable research and development in the area of alternative energy sources. A solar assisted heat pump dryer and water heater found to be one of the solutions while exploring for alternative energy sources. The heat pump system is used for drying and water heating applications with the major share of the energy derived from the sun and the ambient. The solar assisted heat pump dryer and water heater has been designed, fabricated and tested. The performance of the system has been investigated under the meteorological conditions of Singapore. The system consists of a variable speed reciprocating compressor, evaporator-collector, storage tank, air cooled condenser, auxiliary heater, blower, dryer, dehumidifier, and air collector. The drying medium used is air and the drying chamber is configured to carry out batch drying of good grains. A water tank connected in series with the air cooled condenser delivers hot water for domestic applications. The water tank also ensures complete condensation of the refrigerant vapour. A simulation program is developed using Fortran language to evaluate the performance of the system and the influence of different variables. The performance indices considered to evaluate the performance of the system are: Solar Fraction (SF), Coefficient of Performance (COP) and Specific Moisture Extraction Rate (SMER). A COP value of 7.5 for a compressor speed of 1800 rpm was observed. Maximum collector efficiencies of 0.86 and 0.81 have been found for evaporator-collector and air collector, respectively. A value of the SMER of 0.79 has been obtained for a load of 20 kg and a compressor speed of 1200 rpm
[en] Highlights: • The optimum combination will provide around 89% of the total load. • The system has a savings during the life cycle with least payback period of 4.37 year. • The optimal system is insensitive to the variation in fuel inflation and discount rate. - Abstract: This paper presents an economic optimization of evaporator and air collector area of a solar assisted heat pump drying system. Economic viability of solar heating systems is usually made by comparing the cost flows recurring throughout the lifetime of the solar and conventional alternative systems. Therefore, identification of optimum variables by using a simulation program and an economic analysis based on payback period of the system are presented in this paper. FORTRAN language is used to run the simulation. Effect of load and different economic variables on payback period is also investigated. Economic analysis reveals that system has sufficient amount of savings during the life cycle with a minimum payback period of about 4 years
[en] Highlights: • The exergy-electrical analogy is developed for energy systems used in buildings. • This analogy has been developed for a complete set of system arrangement options. • Different possibilities of inter-connections are illustrated using analog switches. • Adaptability and utility of the diagram over traditional ones are emphasized. - Abstract: An exergy-electrical analogy, similar to the heat transfer electrical one, is developed and applied to the case of integrated energy systems operating in buildings. Its construction is presented for the case of space heating with electric heaters, heat pumps and solar collectors. The proposed analogy has been applied to a set of system arrangement options proposed for satisfying the building heating demand (space heating, domestic hot water); different alternatives to connect the units have been presented with switches in a visualization scheme. The analogy for such situation has been performed and the study of a solar assisted heat pump using ice storage has been investigated. This diagram directly permits energy paths and their associated exergy destruction to be visualized; hence, sources of irreversibility are identifiable. It can be helpful for the comprehension of the global process and its operation as well as for identifying exergy losses. The method used to construct the diagram makes it easily adaptable to others units or structures or to others models depending on the complexity of the process. The use of switches could be very useful for optimization purposes
[en] There are reviewed the healing elements of four 'solar houses', situated on 50, 52 and 53 degrees northern latitude in France and England. The use of an extra energy source is shown: such as caldron (house in Milton-Caines), a thermal pump (Rickmansworth house) electric tiers (house in Englesi). The relation between the collector surface and the surface of the floor is indicated In tables are given the basic parameters of the elements
[en] A solar assisted heat pump dryer has been designed, fabricated and tested. This paper presents the performance of the evaporator-collector and the air collector when operated under the same meteorological conditions. ASHRAE standard procedure for collector testing has been followed. The evaporator-collector of the heat pump is acting directly as the solar collector, and the temperature of the refrigerant at the inlet to the evaporator-collector always remained below the ambient temperature. Because of the rejection of sensible and latent heats of air at the dehumidifier, the temperature at the inlet to the air collector is lower than that of the ambient air. Hence, the thermal efficiency of the air collector also increases due to a reduction of losses from the collector. The efficiencies of the evaporator-collector and the air collector were found to vary between 0.8-0.86 and 0.7-0.75, respectively, when operated under the meteorological conditions of Singapore