Results 1 - 1 of 1
Results 1 - 1 of 1. Search took: 0.023 seconds
[en] On 27 Nov. 2007, during a non-routine walkdown of the off-site switchyard to investigate line voltage differences, the licensee discovered that the Phase A conductor of a 138 kV off-site power circuit of the Beaver Valley Power Station Unit 1 had broken off in the switchyard. This break occurred between the off-site feeder breaker and the line running on-site to the A train system station service transformer, located inside the site security fence. The terminal broke on the switchyard side of a revenue-metering current transformer/voltage transformer installed in 2006 to track the station’s power usage through this line. During normal power operation, no appreciable current goes through this 138 kV line because the unit generator normally powers the station buses (loads). The licensee determined that the break on the 138 kV Phase A had occurred 26 days earlier and, therefore, had not been restored within 72 h as required by technical specifications.